The AF12301013 is a 3 pole  690 V IEC or 600 UL contactor with 1 builtin auxiliary contact and screw terminals, controlling motors up to 5.5 kW / 400 V AC (AC3) or 71/2 hp / 480 V UL and switching power circuits up to 28 A (AC1) or 28 A UL general use. Thanks to the AF technology, the contactor has a wide control voltage range (100250 V 50/60 Hz and DC), managing large control voltage variations, reducing panel energy consumption and ensuring distinct operations in unstable networks. Furthermore, surge protection is builtin, offering a compact solution. AF contactors have a block type design, can be easily extended with addon auxiliary contact blocks and an additional wide range of accessories.
Specifications
Dimensions 


Product Net Width  45 mm 
Product Net Depth / Length  77 mm 
Product Net Height  86 mm 
Technical 

Number of Main Contacts NO  3 
Number of Main Contacts NC  0 
Number of Auxiliary Contacts NO  1 
Number of Auxiliary Contacts NC  0 
Standards  IEC 609471 / 6094741 and EN 609471 / 6094741, UL 508, CSA C22.2 N°14 
Rated Operational Voltage  Auxiliary Circuit 690 V Main Circuit 690 V 
Rated Frequency (f)  Auxiliary Circuit 50 / 60 Hz Main Circuit 50 / 60 Hz 
Conventional Freeair Thermal Current (I_{th})  acc. to IEC 6094741, Open Contactors q = 40 °C 35 A acc. to IEC 6094751, q = 40 °C 16 A 
Rated Operational Current AC1 (I_{e})  (690 V) 40 °C 28 (690 V) 60 °C 28 A (690 V) 70 °C 24 
Rated Operational Current AC3 (I_{e})  (415 V) 60 °C 12 A (440 V) 60 °C 12 A (500 V) 60 °C 12.5 A (690 V) 60 °C 9 A (380 / 400 V) 60 °C 12 A (220 / 230 / 240 V) 60 °C 12 A 
Rated Operational Power AC3 (P_{e})  (400 V) 5.5 kW (415 V) 5.5 kW (440 V) 5.5 kW (500 V) 7.5 kW (690 V) 7.5 kW (380 / 400 V) 5.5 kW (220 / 230 / 240 V) 3 kW 
Rated Operational Current AC15 (I_{e})  (500 V) 2 A (690 V) 2 A (24 / 127 V) 6 A (220 / 240 V) 4 A (400 / 440 V) 3 A 
Rated Shorttime Withstand Current Low Voltage (I_{cw})  at 40 °C Ambient Temp, in Free Air, from a Cold State 10 s 150 A at 40 °C Ambient Temp, in Free Air, from a Cold State 15 min 35 A at 40 °C Ambient Temp, in Free Air, from a Cold State 1 min 60 A at 40 °C Ambient Temp, in Free Air, from a Cold State 1 s 300 A at 40 °C Ambient Temp, in Free Air, from a Cold State 30 s 80 A for 0.1 s 140 A for 1 s 100 A 
Maximum Breaking Capacity  cos phi=0.45 (cos phi=0.35 for Ie > 100 A) at 440 V 250 A cos phi=0.45 (cos phi=0.35 for Ie > 100 A) at 690 V 106 A 
Maximum Electrical Switching Frequency  (AC1) 600 cycles per hour (AC15) 1200 cycles per hour (AC2 / AC4) 300 cycles per hour (AC3) 1200 cycles per hour (DC13) 900 cycles per hour 
Rated Operational Current DC13 (I_{e})  (24 V) 6 A / 144 W (48 V) 2.8 A / 134 W (72 V) 1 A / 72 W (110 V) 0.55 A / 60 W (125 V) 0.55 A / 69 W (220 V) 0.27 A / 60 W (250 V) 0.27 A / 68 W (400 V) 0.15 A / 60 W (500 V) 0.13 A / 65 W (600 V) 0.1 A / 60 W 
Rated Insulation Voltage (U_{i})  acc. to IEC 6094741 and VDE 0110 (Gr. C) 690 V acc. to UL/CSA 600 V 
Rated Impulse Withstand Voltage (U_{imp})  6 kV 
Maximum Mechanical Switching Frequency  3600 cycles per hour 
Rated Control Circuit Voltage (U_{c})  50 Hz 100 ... 250 V 60 Hz 100 ... 250 V DC Operation 100 ... 250 V 
Operate Time  Between Coil Deenergization and NC Contact Closing 13 ... 98 ms Between Coil Deenergization and NO Contact Opening 11 ... 95 ms Between Coil Energization and NC Contact Opening 38 ... 90 ms Between Coil Energization and NO Contact Closing 40 ... 95 ms 
Mounting on DIN Rail  TH357.5 (35 x 7.5 mm Mounting Rail) acc. to IEC 60715 TH3515 (35 x 15 mm Mounting Rail) acc. to IEC 60715 
Mounting by Screws (not supplied)  2 x M4 screws placed diagonally 
Connecting Capacity Main Circuit  Flexible with Ferrule 1/2x 0.75 ... 6 mm² Flexible with Insulated Ferrule 1x 0.75 ... 4 mm² Flexible with Insulated Ferrule 2x 0.75 ... 2.5 mm² Rigid 1/2x 1 ... 6 mm² 
Connecting Capacity Auxiliary Circuit  Flexible with Ferrule 1/2x 0.75 ... 2.5 mm² Flexible with Insulated Ferrule 2x 0.75 ... 1.5 mm² Flexible with Insulated Ferrule 1x 0.75 ... 2.5 mm² Rigid 1/2x 1 ... 2.5 mm² 
Connecting Capacity Control Circuit  Flexible with Ferrule 1/2x 0.75 ... 2.5 mm² Flexible with Insulated Ferrule 1x 0.75 ... 2.5 mm² Flexible with Insulated Ferrule 2x 0.75 ... 1.5 mm² Rigid 1/2x 1 ... 2.5 mm² 
Wire Stripping Length  Auxiliary Circuit 10 mm Control Circuit 10 mm Main Circuit 10 mm 
Degree of Protection  acc. to IEC 60529, IEC 609471, EN 60529 Auxiliary Terminals IP20 acc. to IEC 60529, IEC 609471, EN 60529 Coil Terminals IP20 acc. to IEC 60529, IEC 609471, EN 60529 Main Terminals IP20 
Terminal Type  Screw Terminals 